Not every project goes as well as planned. We would be happy to spend a few minutes answering your questions.
A customer was out of town for a few days and came back to discover that the toilet bowl was empty. Usually there is standing water in the bowl, but it was dry. She called her favorite Las Vegas handyman to determine why.
There are only a few reasons why this would happen. The first reason turned out to be the cause. The had a crack in the trapway of the toilet, which caused the water to drain out into the drain pipe below. This wasn't obvious because the crack was centered over the drain, and therefore didn't leave any water around the base of the toilet. Since the crack was small, it took some time for it to go dry. Naturally, if the toilet is being used regularly, the bowl will get refilled after each use, and you probably wouldn't notice a slightly lower water level. However, when the toilet wasn't used for a few days, it had time to go completely dry. The fix here was to replace the toilet bowl.
Another reason a toilet bowl will be dry is due to the vent. Drains require air, and the vent provides this. If the vent is clogged then as the water goes down the drain it tends to pull air with it from any source. This creates a siphon and pulls the water left in the bowl down with it. It won't pull all of the water down with it, but if the toilet is not used for a while the small amount of remaining water may evaporate. The fix for this would be to clear the vent from the roof.
Allowed tags: <a> link, <b> bold, <i> italics
© 2014 Pro Handyman Corp • PO Box 96761 • 1001 E. Sunset Rd • Las Vegas, Nevada • 89193 Lic. #'s 50937 & 55184 Copyright © 2003-2009 Pro Handyman Corporation. All rights Reserved. Please direct questions and comments to firstname.lastname@example.org